Should be selected based on their BTU/KW output and the recommended maximum area specified for that output. Should be selected based on the sum of the above. A multi split system consists of 3 separate areas.The cooling load of each area = 9000BTU, 12000BTU and 18000BTU. Three indoor units will be required as follows, eg. KFR-23IW/X1c-M-IU Wall Split 9000BTU 2.7Kw Heat & Cool Air Conditioning Inverter System Indoor Unit Only. KFR-33IW/X1c-M-IU Wall Split 12000BTU 3.5Kw Heat & Cool Air Conditioning Inverter System Indoor Unit Only. KFR-53IW/X1c-M-IU Wall Split 18000BTU 5Kw Heat & Cool Air Conditioning Inverter System Indoor Unit Only. Based on this, the outdoor condenser should have a minimum output of 39000BTU total. Therefore, for this 39000BTU cooling load select the following condenser. 5 Head Outdoor Unit 41000 BTU Total Capacity. Please note that If the condenser is undersized then (assuming no diversity) the output of the indoor units will be proportionally reduced. The KFR Series of Split Systems are designed for Easy Fit and speedy installation, however this does not mean that you are allowed to fully install these units yourself. It is a legal requirement that all EasyFit units must be at least commissioned by an F Gas Registered Engineer.
Two Air Conditioning Centre warranties are available. (i) Installed by F-Gas registered installer.
(ii) Serviced by F-Gas registered installer. If you dont have an F Gas installer, we will be pleased to help you find those local to you who can offer a commissioning or full installation service. Kits of 2m/4m/6m are available.
Other KFR multi split series indoor models available. 9000BTU 2.7Kw Heat & Cool Air Conditioning Inverter System Indoor Unit Only. KFR-50QIW/X1c-M-IU Ceiling Cassette 18000BTU 5Kw Heat & Cool Ceiling Cassette Air Conditioning Inverter System Indoor Unit Only.
KFR-37CIW/X1c-M-IU Console 12000BTU 3.5Kw Heat & Cool Console Air Conditioning Inverter System Indoor Unit Only. KFR-57CIW/X1c-M-IU Console 18000BTU 5Kw Heat & Cool Console Air Conditioning Inverter System Indoor Unit Only. Single outdoor units available for use with the above indoor units. KMS-3MIO/X1C 3 Head Outdoor Unit 27000 BTU Total Capacity.4 Head Outdoor Unit 36000 BTU Total Capacity. KMS5MIO/X1C 5 Head Outdoor Unit 42000 BTU Total Capacity. F Gas Regulations Legal Requirement : Any split style air conditioning unit must be installed by an F-Gas qualified engineer. We can arrange to install the unit for you using an F-Gas Certified Engineer. This is a requirement of the Article 11 (5) EC/517/2014 on fluorinated greenhouse gases and The Fluorinated Greenhouse Gases Regulations 2015. Whilst every attempt is made to ensure the accuracy of information contained on this site¸ errors can occasionally occur. My Personal Climate cannot accept any responsibility for any reliance upon such information¸ any omissions or any subsequent loss or damage. By providing information on this site¸ My Personal Climate is in no way recommending that any unqualified person undertake the installation¸ servicing or other mechanical repair of any Air Conditioning System, Heat Pump or Air Purifier. My Personal Climate reserves the right to amend¸ update or withdraw any information on this site without prior notice. The item "Air Conditioning Multi- Split Systems KFR-53IWithX1c/18000BTU (Indoor unit only)" is in sale since Thursday, April 15, 2021. This item is in the category "Home, Furniture & DIY\Heating, Cooling & Air\Air Conditioners\Ductless Mini Split Systems". The seller is "my_personalclimate" and is located in Cheshire. This item can be shipped to United Kingdom.